AWC'sare highly effective for removing even the most stubborn scales and foulants from RO/NF membranes. Our membrane cleaning chemicals are formulated for all types of RO membrane systems, ranging from those used in Food and Beverage applications to Water Reuse applications.The outcome of a membrane cleaning is equally dependent on procedure as it is on the quality of the cleaning chemical. However, an optimal procedure isn’t always possible to implement due to limitations in the design of the Clean-In-Place (CIP) system. AWC can provide recommendations on CIP system design, and can provide training on best practices and procedures to enhance RO membrane cleaning results and to reduce frequency of CIP’s. Additionally, we offer cleaning studies that allow us to identify the optimal temperature, pH and cleaning time for the membrane foulant in your specific system.High pH and low pH chemicals are available in both liquid and powder form.All of AWC's cleaning chemicals are NSF approved for use in potable membrane systems.
RO membrane cleaning should be performed with high and low pH CIP chemicals. The high pH cleaning should always be performed first to penetrate and disperse biological or organic foulants. Specialty high pH cleaning chemicals more effectively penetrate heavy organic and biological foulants, making them more effective than commonly used CIP chemicals such as sodium hydroxide. While many choose the lowest cost CIP chemicals, their annual cost will end up being significantly higher because of the higher frequency of cleaning, this incurs more labor costs, chemical costs, and downtime. It’s always best to perform a cleaning study to ensure that membrane performance is fully restored after CIP.
The use of citric acid is recommended prior to high pH cleaning by some companies, due to its chelating properties. We strongly recommend against this practice – Organic foulants lose their anionic charge if a low pH cleaning is performed first, and since some permeate is almost always produced during CIP, the foulants will be compacted into the membrane and become more difficult to penetrate.
What is the Best Method for Cleaning RO Membranes?
Membrane CIP results will be best if each stage is cleaned individually. This will allow for the maximum flow velocity during cleaning. If both stages of a system with a 2:1 array are cleaned simultaneously, each pressure vessel in the second stage will receive twice the flow velocity as the first stage. This would cause membrane telescoping in the second stage if the first stage elements are cleaned at optimal flow velocity. Alternately, by basing the flow velocity on the second stage, the first stage membranes would not receive sufficient surface scouring.
The total volume in the system should always be considered when determining how much CIP chemicals to add. You can use the AWC RO CIP Calculator to help you calculate the correct amount of chem
When performing a cleaning of a RO system, the first 20% of the cleaning solution is flushed through the membranes directly to drain, instead of circulating. This will prevent contamination of the cleaning solution with loose foulants and large suspended solids.
The remaining solution is then circulated through the system while carefully monitoring the pressure differential (dP). dP should not exceed 10 PSI (0.69 bar) per membrane element. Every 30 – 60 minutes, the circulation can be stopped to allow the membranes to “soak” for about 30 – 60 minutes. Circulation should then be started again to flush off the disintegrated foulant and to bring fresh cleaning chemical to the membrane surface. pH should be checked every 15- 30 minutes during circulation. If the pH of the cleaning solution has changed, more cleaning chemical should be added to adjust the pH back to the target range.
Soaking and circulating can be repeated alternately until cleaning is complete. Low pH cleaning is determined to be complete when the pH stabilizes, but the length of a high pH cleaning should be based on a predetermined time. The length of time required for optimal CIP results can either be obtained by trial and error, or by performing a cleaning study.
A high pH cleaning is usually performed at a pH of 11 – 12 using a cleaning chemical such as AWC C-236 for silica, AWC C-237 for biofouling or AWC C-227 for heavy organics fouling. More chemical is added during the cleaning every time the pH drops below 11. If the solution becomes very dark or turbid, it should be drained and a new cleaning solution should be prepared.
A low pH cleaning should be performed at a pH of 2 – 3 using CIP chemicals such as AWC C-234 or AWC C-235 (phosphorous free). If the pH of the cleaning solution increases above 3 at any time during the cleaning, more cleaning chemical must be added to reduce the pH to its target range of 2 – 3.
AWC provides the membrane community with chemical solutions for optimizing RO system operation. Be sure to contact us today at (813) 246-5448 to learn more about our specialty membrane CIP chemicals.
700mm UHP Graphite Electrode 600mm HP Graphite Electrode 450mm RP Graphite Electrode Hot Sale Galvanized Automotive Steel Galvanized Steel Automotive Steel Sheet outdoor research tactical gloves Hand Sanitizer WingFlying Drone Thrust Test Drone Motor Test Stand Drone Test Equipment Box Stitching Machine hydroxypropyl methylcellulose wholesale Methyl Hydroxyethyl Cellulose Hydroxypropyl Methyl Cellulose 2.0 vs 3.0 flash drive